Call 800-916-7873 in the USA
Text your questions to 269-601-4965
Our mission is to rescue the victims of abusive high pressure sales by empowering them with information, rewarding them with savings and retaining them with customer service.
For our Canadian customers, there may be taxes and duties on your shipments now that our operations have moved to the USA. We apologize for any inconvenience.
Compare Electro Breeze V-Banks with Dynamic V8 Electronic Air Cleaner Filters
Shipping is delayed about 3-4 weeks, but if you need a pad right away, just let us know in the special instructions during checkout and we'll get one to you right away at no additional charge.
Thank you for your patience as we follow procedures to ensure the safety of our employees as well as the safety of our customers.
Below, you will find a typical specification for Dynamic V8 electronic air cleaner filters. This specification was also used in a bid with Trane Commercial Air Conditioning for their installation of the Dynamic V8 filters. These are the same Dynamic V8 electronic air cleaner filters specified for the Daikin Air Conditioning package units. You will also see that the specification for this commercial air cleaner is written so that only the Dynamic V8 will meet the requirements. As you can see by comparing with the specifications further down, the Electro Breeze electronic air cleaner offers a better solution at a much better price.
Engineering spec for the Dynamic V8 electronic air cleeaner filters from Trane Commercial Air Conditioning:
The air filtration systems shall be comprised of a bank of electronically active
field polarized media air cleaners manufactured by Dynamic AQS
or approved equal. The filtration units shall be constructed of non-ionizing, polarized-media
electronic air cleaners, Model V8 MERV 15/13 rated per ASHRAE 52.2. The dual rating
of the filters is based on a MERV 15 with power to the assembly and a MERV 13 performance
on a loss of power. Any particulate captured will not drop off the media in a loss
- The air cleaners shall have been tested to meet CSA Standard C22.2 No. 187-M19986
and UL Standard 867 for electrostatic air cleaners.
- The air cleaners shall have an active electrostatic field that polarizes a dielectric
media. It shall not ionize airborne particles or produce ozone.
- Using the ASHRAE 52.2 protocol with no carbon in the loading dust, the air cleaners
shall test at MERV 15. They shall have a clean static pressure drop of .42 in. w.g.
and shall increase in resistance no more than .25 in. w.g. with a dust loading of
2,855 grams. Each air cleaner shall be capable of holding a total of 4,582 grams
of dust at its final resistance of 1.4 in. w.g. per 24x24 module.
- The air cleaner modules shall consist of eight individual air cleaners. The construction
of the air cleaner frame shall be aluminum and screens and side panels shall be galvanized
steel. The air cleaner modules and each component thereof must have a positive seal
where necessary to prevent bypass of air.
- Each air handling units air cleaner high voltage power heads shall require 24 volts
AC input. The power heads must be fully potted and connected in parallel.
- Each air handling units filter unit shall require a single 120VAC power supply,
one connection per air handling unit. The power supply must be a UL or CSA certified
transformer, class 2 type, which shall permit one side of the secondary output, 24V,
to be attached to electrical ground. A NEMA 1 panel rated for 5 amps will be provided.
- Each air cleaner shall have a disposable and recyclable media pad with a minimum
class 2 fire rating. It shall have a positive seal in the overall filter assembly.
- The air cleaners will be arranged in a pre-fabricated module assembly comprised
of eight separate air cleaners and galvanized metal sides and attachment flanges.
Each V Bank module shall be nominal 12, 18 or 24 inches overall height, 26, 30,
34, 39, 43 or 48 inches overall width, and 29.5 inches overall depth. Final module
sizing shall be by the air cleaner unit manufacturer and coordinated with the air
handling units manufacturer so as to assure the filters will fit within the air handling
unit allocated cabinet section, installed in the cabinet section at the air handling
units manufacturers factory, and no additional modifications to the air handling
unit and/or filter units will be required in the field.
Compare with the specifications of the Electro Breeze V-Bank commercial air filters:
The V-Bank module filtration system shall be consist of eight
1-inch electronic air panels of electronically non-ionizing
air cleaner shall have been tested and meet CSA Standard C22.2 and
No 187-M19986 and UL standard 867 for electronic air cleaners.
to the Indoor Air Quality Procedures outlined in the ASHRAE Standard
62-2001, large buildings using the Electro Breeze air cleaner system
may be able to cut their outside air requirements in half or even to
The air cleaner shall have an
active electrostatic field that polarizes a dielectric collector
It shall not ionize airborne particles or produce ozone.
The air cleaner shall be able to remove 97.8% of the airborne
particulates 0.3 micron and greater in a re-circulating system.
Pressure drop across the air cleaner will be no more than 0.2”w.g.
V-Bank module cabinet shall be galvanized steel pre-fabricated
module assembly. It shall be pre-fabricated to permit the assembly
at the HVAC manufacturing plant. The air cleaner module shall
consist of eight individual air cleaners. The
construction of the air cleaner frame and screens shall be
aluminum. A miniaturized electronic power supply (power head)
shall be mounted in a channel on the frame of the air cleaner in a
non-conductive housing. A folding glass fiber media that create
two pads shall be placed between the outside grounded frame/screens
and the center collector cushion carbon. The center collector
cushion carbon or mesh shall carry the high DC voltage from the
power head. The air cleaner frames shall be hinged so as to allow
easy access to the media pad for replacement. Each
1-inch panel can be removed by sliding out each one for yearly
maintenance or future full inspection.
The power heads shall be capable of converting 24VAC to the 7.2 kVDC and draw no more than two watts of power. The power head
shall be insulated from the air cleaner frame and it shall transmit
the 7.2 kVDC to the center collector cushion activated carbon of
the media pad through a special copper filament. Each air cleaner
shall have a “Power On” lamp and be equipped with a
high-voltage resistor to de-energize the air cleaner when the power
is shut off. The power heads will be connected in parallel so that
if one fails, it will have no effect on the other power heads in
Supply: The 24VAC power supply must be a UL or CSA certified
transformer, class “2” type, which shall permit one side of the
secondary output (24V) to be attached to electrical ground.
Cleaner Media: Replaceable air cleaner collector cushion pad shall
be individual, disposable glass fiber “collector cushion”,
which shall consist of a folded glass fiber pad that create two ply
of fiber glass with a conductive center activated carbon or
aluminum mesh. This conductive center carbon or mesh shall be
permanently enclosed between the folded pad that makes two pieces
of fiberglass and shall be disposed of when the collector cushion
pad is changed. The glass fiber pad must be fabricated from a
constant filament so that any shed fibers are not enhanced. The
glass fiber must have a minimum of a class “2” fire rating.
air cleaner shall have installed either a carbon or aluminum mesh
core collector cushion pad.
Feel free to contact us with your questions or your request for quote at 800-916-7873 or email at firstname.lastname@example.org
Engineering specifications for all of the Electro Breeze air cleaner products can be found here.